Navi
ID : 6805
LED 3000K, 4000K, 5700K 230-240Vac CRI >80 MacAdam step 3
Input power : 45W
Dimension : 166 x 168 x 584mm
Beam angle : 10° / 28° / 45°
Electronic driver ON/OFF
CE and BIS

LUMINAIRE TYPE
Flood Light. IP rating IP65
MATERIAL CHARACTERISTICS
Extruded aluminium bottom pipe (grade 6063 with test certificate) Ø100 x 2.5mm thickness & extruded aluminium hood cover(grade 6063 with test certificate) Ø166 x 3mm thickness. Module fixing clamp made of galvanized CRCA sheet 3mm thickness. SS fasteners. Clear silicone gaskets. Die-cast aluminium mounting plate Ø100.5 x 4mm thick with 2 elongated holes 15 x 10 to suit  M8 bolts at PCD 55 with pure polyester powder coating. This mounting plate along with foundation bolts of suitable size to be used for ensuring firm grouting into the specially designed foudation. Hot dip galvanised foundation bolt. Mechanical resistance IK07.
Pure polyester powder coated process : Acid treatment & pure polyester powder coating.
LIGHTING PERFORMANCE
Clear polycarbonate optical cover with light emission at desired angle. Lamp fixed position.
Navi 
This luminaire contains built-in LED modules. LED modules are engineered accordingly to the existing regulations of Lumen Maintenance (LM80) and Technical Memorandum (TM21), Lifespan of the luminaire > 60,000 hours at 40°C. Operating ambient temperature range is from -15°C to +50°C. Driver efficiency >85%, power factor >0.9, THD <10%, Surge protection 6KV. 