Column Light
ID : 27018
LED 2700K, 3000K, 4000K, 5700K 230-240Vac CRI >80 MacAdam step 3
Input power : 90W
Height  4200mm
Light Distribution  360°
Electronic driver ON/OFF
CE and BIS

LUMINAIRE TYPE
Light Column. IP rating IP65
MATERIAL CHARACTERISTICS
Extruded aluminium bottom ribbed pipe (grade 6063 with test certificate) Ø166 x 3mm thickness & die-cast aluminium top cover. SS fasteners. Pre treated silicone gaskets. PDC aluminium service door 348mm height x 110mm width at 338mm height above the base plate shall be provided with the company logo embossed on the bottom of the door and safety rope. The control gear tray is prewired with 2.5 Sq.mm cable, 6A MCB and 32A terminal connectors for loop-in / loop-out arrangement.
MS mounting plate Sq. 250 x 12mm thick steel of grade E250 to IS 2062:2011 with 4 elongated holes 38 x 19 to suit M16 bolts at CC180. This mounting steel plate along with foundation bolts of suitable size to be used for ensuring firm grouting into the specially designed foundation pole. Hot dip galvanised foundation bolt. Mechanical resistance IK08.
Pure polyester powder coated process : Mild shot blast &  pure polyester powder coating.
LIGHTING PERFORMANCE
Translucent polycarbonate diffuser of 3mm thickness with  light emission. Lamp fixed position.
COLUMN LIGHT
This luminaire contains built-in LED modules. LED modules are engineered accordingly to the existing regulations of Lumen Maintenance (LM80) and Technical Memorandum (TM21), Lifespan of the luminaire > 60,000 hours at 40°C. Operating ambient temperature range is from -15°C to +50°C. Driver efficiency >85%, power factor >0.9, THD <10%, Surge protection 6KV. 